# DP calculator for open tank level measurements

Basic level measurement is done using open tank level. Its calculation is relatively easy and is shown below.

**Zero based direct mount application**

The level transmitter is positioned in the same level position as the HP tapping point when it is connected.

Pressure on H.P. side of transmitter P.HP = Patm + (SG*h)

Pressure on LP side of the transmitter P.LP= Patm(open to atmospheric pressure)

The transmitter’s differential pressure is calculated as follows:

DP = P.HP – P.LP

DP = Patm + (SG*h) â€“ Patm

DP = SG*h

**LRV Calculation**

In order to obtain LRV, the pressure on the HP side and LP side of the tank must be empty. When the tank is empty, there will be no pressure on either the HP side or the LP side. since there will be no liquid height.

So h = 0

Then DP = Patm+(SG*h) â€“ Patm

PH.P = Patm + (SG*0)

=Patm

PL.P = Patm

LRV = PH.P. â€“ PL.P

= Patm â€“ Patm

LRV=0

**Estimating the URV**

When the tank is completely full of liquid (h), determine the transmitter’s differential pressure (DP).

PH.P = Patm +(SG*h)

PL.P = Patm

URV = P.HP â€“ P.LP

= Patm+(S.G*h) â€“ Patm

URV = S.G*h

**Range of the transmitter = 0 to (S.G*h)**

## DP calculator

Click here for moreÂ **Instrumentation Calculators**